Many air conditioning systems incorporate a hermetic (welded body) compressor as the standard. It is extremely important for the HVAC technician to identify the correct
electrical terminals. If the electrical terminals are not wired correctly, severe compressor or system damage will result. A standard has been developed for single phase welded compressors. The standard terminal designation is read like a book, from left to right and from top to bottom. The order of these terminals is Common (C) - Start (S) - Run (R). While protectors are very reliable and do a good job of protecting a compressor motor against normal overload situations, they cannot protect motors against miswiring and defective external components. Miswiring a compressor can cause a motor to burn in as little as 25 seconds. Any motor miswired or used with defective components will ultimately fail. Be sure to check or replace any electrical components including but not limited to the contactor, run capacitor, relay, and start capacitor. Any of these ccomponents could also cause compressor failure.
Disclaimer: The information provided within this publication / eBook/ content is for general informational purposes only. While we try to keep the information up-to-date and correct, there are no representations or warranties, express or implied, about the completeness, accuracy, reliability, suitability or availability with respect to the information, products, services, or related graphics contained in this publication / eBook/ content for any purpose. Any use of this information is at your own risk.